Instrumentation cables manufactured in accordance with British Standard BS5308
Whilst this British Standard was superseded by the Harmonised Standard BS EN 50288-7 in 2005 it is still widely referred to because the Harmonised Standard does not account for the higher voltage ratings and cable dimensions. A publicly available version of the Standard was published as PAS5308 in 2009.
British Standard BS5308 covers specifications for a range of instrumentation cables which we supply. These are available in a multitude of variants including Polyethylene (PE), Polyvinyl Chloride (PVC), Cross-Linked Polyethylene (XLPE), and Low Smoke Zero Halogen (LSZH) insulation materials, and armoured instrumentation cables.
BS5308 Part 1 Type 1 - Unarmoured - collectively screened (CAM) and individually & collectively screened (IAM/CAM or ICAT). PE insulated and PVC oversheathed.
BS5308 Part 1 Type 2 - Armoured - collectively screened and also individually & collectively screened. PE insulated, PE bedded, single wire armoured (SWA) and PVC oversheathed.
BS5308 Part 1 Type 3 - Armoured - collectively screened or individually & collectively screened. PE insulated, PVC bedded, lead alloy oversheath, single wire armoured and PVC oversheathed.
BS5308 Part 2 - PVC insulated instrumentation cables - British Standard BS5308 Part 2 specifies requirements for PVC insulated cables, in multicore and multi-pair construction, with or without screens. It provides the option to incorporate a single wire armour. Part 2 is further categorised as Types 1 & 2.
BS5308 Part 2 Type 1 - Unarmoured construction - PVC insulated and PVC oversheathed.
BS5308 Part 2 Type 2 - Armoured construction - PVC insulated, PVC bedded, single wire armoured and PVC oversheathed.
Construction comparison of BS5308, PAS5308 and BS EN 50288-7
|Conductor||Plain annealed copper, solid or stranded (BS6360)||Plain annealed copper, stranded (BS6360)||Plain annealed copper, multi-stranded (BS EN 60228)||Plain annealed copper, multi-stranded (BS EN 60228)||Plain annealed or metal-coated, solid or stranded (IEC 60288)|
|Conductor size||0.5mm2 to 1.5mm2||0.5mm2 to 1.5mm2||0.5mm2 to 2.5mm2||0.5mm2 to 2.5mm2||0.5mm2 to 4.0mm2|
|Voltage range||300/500V||300/500V||300/500V||300/500V||90V, 300V, 500V|
|Insulation||PE Type 03||Polyvinyl Chloride (PVC) Type TI1||Thermoplastic PE or Cross-linked Polyethylene (XLPE)||PVC Type TI51||PVC, PE, XLPE, Polypropylene or Halogen-free flame retardant compound|
|Formation||Core pair twisted quad||Core pair twisted quad||Core pair twisted quad||Core pair twisted quad||Twisted core pair, triple or quad|
|Individual and/or Screen||Aluminium foil laminate tape (PET)||Al/PET||Al/PET||Al/PET||Al/PET|
|Drain Wire||Solid or stranded tinned annealed copper||Solid or stranded tinned annealed copper||Solid or stranded tinned annealed copper||Solid or stranded tinned annealed copper||Solid tinned copper|
|Braid||Not defined||Not defined||Not defined||Not defined||Tinned copper wires|
|Covering||Not defined||Not defined||Not defined||Not defined||Lead sheath to EN 50307|
|Inner Sheath||Extruded PE compound Type 2C or Extruded Polyvinyl Chloride (PVC) Type TM1||Extruded PVC Type TM1||Extruded PE compound Type 2 or Extruded PVC Type TM51||Extruded PVC Type TM51||PVC, PE or Low Smoke Zero Halogen (LSZH) compound|
|Armour||Galvanised steel wire armour (GSWA)||GSWA||GSWA||GSWA||Steel wire armour (SWA)|
|Moisture barrier||Not defined||Not defined||Not defined||Not defined||Water-swellable tape, water-swellable non-toxic powder, filling compound, laminated sheath of a longitudinally overlapped metallic foil, or a combination of all|
|Outer sheath||Extruded Polyvinyl Chloride (PVC) Type TM1||Extruded PVC Type TM1 (type 1 & 2)||Extruded PVC Type TM51||Extruded PVC Type TM51||PVC, PE or Low Smoke Zero Halogen (LSZH) compound|
BS5308 cable colour coding
Our extensive portfolio is backed by a wide range of services that help your project run smoothly, together providing a complete cable solutionLearn more
Learn more about our UKAS accredited ISO 17025 testing laboratory, our specialist MV test facility, and the tests that provide quality and compliance assuranceRead on
Use our cable calculator to aid with cable sizing in accordance with British BS7671 and International IEC 60364-5-52 standardsCalculate cable size