FAQ: What are the main causes of electrical cable failure?
There are many reasons why a cable may fail in service, with the failure at its most serious resulting in fire or other serious fault.
Some of the main causes of cable failure include:
The service life of a cable can be significantly reduced if it has been expected to operate outside of the optimal operating conditions it was designed for. The ageing process usually results in embrittlement, cracking and eventual failure of the insulating and sheathing materials, exposing the conductor and risking a potential short circuit, a likely cause of electrical fire.
If cable selected is not appropriate for the application it is more likely to fail in service. For example, a cable which is not robust enough for the environment, either mechanically tough enough to wear and abrasion or chemically resistant to the ambient conditions, is more likely to fail than one whose construction is suitable for the installation environment.
If the cable is damaged either during installation or in subsequent use, the integrity of the cable will be affected and reduce its service life and suitability.
Degradation of the cable sheath:
There are several reasons why the sheathing material may degrade, including excessive heat or cold, chemicals, weather conditions, and abrasion of the sheath. All of these factors can ultimately cause electrical failure as the insulated cores are no longer protected by the sheathing as originally designed.
Moisture in the insulation:
Moisture ingress can cause significant problems including short circuit and corrosion of the copper conductors.
Heating of cable:
Excessive heating of the cable will cause degradation of the insulation and sheathing material and premature failure. The heat may come from an external source or may be generated by the resistance to current flow in the conductor - a particular problem if the cable is overloaded and/or underrated for the application.
Electrical overloading normally occurs when the cable is underrated for the application or when too much load is being placed on the cable. In domestic applications this is often a result of plugging too many appliances into the one socket and overloading the wiring to that individual socket, extension adaptor or gang socket.
Rodents frequently attack the outer layers of cables. This damage can be extensive, significantly reducing the sheathing or insulation properties of the cable, another likely source of electrical fires.
UV exposure can have a significant influence on electrical cable insulation and sheathing. Cables likely to be exposed to UV light should either be designed with UV resistant materials with a suitable carbon black content, or protected from exposure with a protective covering such as installing inside cable conduit so not in direct sunlight. UV exposure frequently causes cracking of the insulation and therefore potential short circuit failures.
Call Sales on +44 (0)20 7241 8787
Click to Email Us We will reply within 3 hours
Technical Hotline +44 (0)20 7241 8500
The Cable Lab®
UKAS-accredited specialist cable testing laboratory
The Cable Lab® our in-house cable testing facility, is UKAS-accredited to ISO 17025, which is the single most important standard for calibration and testing laboratories around the world. Accreditation to this international standard demonstrates our laboratory's technical competence and the accuracy of its results.
For our customers, it means peace of mind. They can have full confidence in the quality of our products and can demonstrate due diligence in selecting their cable supplier.
Our customers can also rely on the Cable Lab's services for an independent, objective and comprehensive quality assessment of cables procured from third parties.
About Eland Cables
Established in 1975, Eland Cables is a supplier of power, data, instrumentation and control cables and cable accessories to the world's most demanding industries and to some of its most prestigious projects. Our reputation is built on an unswerving focus on quality, technical expertise and customer service.
Our focus on quality has resulted in our in-house specialist cable testing facility securing the ISO 17025 accreditation. This certifies the competence, impartiality and performance capability of our laboratory and its evaluations. In turn, it means peace of mind for our customers with regard to the quality of the cables they source from us.
Our highly-qualified technical team is on hand to provide technical support with all aspects of cable selection, technical specification, regulatory requirements, and bespoke cable design and manufacture.
We are a key contributor to projects in over 100 countries every year, adding value through comprehensive technical support, reliable logistics, innovative solutions, and a customer-centric approach.