What is voltage drop?
A voltage drop in an electrical circuit normally occurs when a current passes through the cable. It is related to the resistance or impedance to current flow with passive elements in the circuits including cables, contacts and connectors affecting the level of voltage drop. The longer the circuit or length of cable the greater the voltage loss. The impact of a voltage drop can cause problems such as motors running slowly, heaters not heating to full potential, lights being dimmed. To compensate for voltage drop larger cross-sectional sized cables may be used which offer less resistance / impedance to current flow.
Voltage drop can be calculated from the formula:
Vd =mV/A/m x I x Ib ÷ 1000
mV/A/m = the voltage drop per metre per amp
I = the length of the circuit conductor
Ib = the design current
The allowable voltage drop for low voltage installations supplied directly from a public low voltage distribution system is 3% for lighting and 5% for other uses.
People also ask
The voltage rating of a cable is the highest voltage that may be continuously applied to a cable construction in compliance with the relevant cable standard or specification...
The volt (symbolized V) is the Standard International (SI) unit of electromotive force or the potential difference required to carry 1 ampere of current through a resistance of 1 Ohm...
Electrical conductivity and conductor resistivity are essentially the opposite of each other: Electrical conductivity is the ability of a material to conduct an electrical current...
View our comprehensive range of power, data, control and instrumentation cables and accessoriesGo
Read more on the different tests we conduct in our Cable Laboratorythe Tests
Read about some of the projects we've worked on, spanning all industriesRead on